I've searched the web for an answer to this question, but have yet to find it! What does the NEC say is the maximum distance from the meter to the main panel (assuming the main breaker is in the panel, not at themeter)? Thanks in advnace!
ask your local electrical inspector.ducttapeguy said:Thanks for the link, it was very interesting! (I am the original poster - I have since determined that this is probably a worthwhile place to become a registered user!)
Unfortunately, all I was able to find was this (generic) statement:
The disconnecting means shall be nearest the point of entrance
of the service conductors at a readily accessible location either inside
or outside of the building.
Do you know of anything more specific?