Hello people!!!! this site amazes me with all the homeowner questions. the leveling of the air handler is a good start, but only to a homeowner. Coming from a a/c contractor you guys need to check the obvious things first. like that piece of p.v.c. drain line coming out of the air handler thats the drain line. if it gets plugged then the water has nowhere to go except into the aux. drain pan. wich should have another piece of p.v.c. drain coming out of into a conspicuous location like outside over the kitchen window or something. you need to take a shop vac and hook it up to the drain line outside the house normaly by the condensor and see if you have a blocked drain line, normally you will get an algee build up in these lines and cause a restriction. and end up causing a mess.
Contractor Talk - Professional Construction and Remodeling Forum
A forum community dedicated to professional construction and remodeling contractors. Come join the discussion about the industry, trades, safety, projects, finishing, tools, machinery, styles, scales, reviews, accessories, classifieds, and more!