Hey guys we just completed a basement finishing job. It appears my electrician has one individual circuit for the room. It has 2 can light individually switched, exhaust fan, and light also switched seperatley. The problem is that almost everytime you have everything on and shut the exhaust fan off it trips the GFCI. Should I be worried or is this an easy fix my electrician has always been good in the past. The job is complete except for this and I am nervous. I dont want to tear everything a part but dont want a liabilty either. He keeps saying its not gonna be a big deal. BUt I am worried.